The automatic roller shutter filter ordered by Suzhou Fuxing Sewage Plant has been delivered
Device Name: Automatic Rolling Shutter Filter
HICLOVER is growing brand for environmental protection field, and market share with most of Africa, Middle East, Southeast Asia countries and part of North America, Europe territory. We are trusted partner for governmental organizations, non-profit organizations, international contractors, logistics organizations, military, pet cremation business owners, etc. We have export experience more than 40 countries, including war zone like Iraq, Afghanistan, Somalia, South Sudan. Mobile: +86-13813931455(WhatsApp) Website: www.hiclover.com Email: firstname.lastname@example.org Email: email@example.com
Number of equipment: 3 sets
Shipping Date: December 24, 2021
According to the demand air volume, hole size, filtration category and other information provided by the customer, the automatic rolling shutter filter is designed for filtration. The outer frame material: high-quality aluminum alloy material, the control system: the control system: Siemens automatic and manual control system, the use of G3 filter cotton for filter, equipment size: 2000W*2100H*650D 3 sets.
Filtration and Control Principles
When the air containing dust passes through the filter, the dust is blocked in the fiber layer of the filter material. When the resistance of the fiber layer increases to the upper limit differential pressure value due to agglomeration of dust, the automatic control system starts to start the motor, and automatically winds up to replace the clean filter material, so that the filter remains in a normal resistance state, thereby ensuring the normal operation of the ventilation system.
①Manual control method: the user can press the motor switch at any time to replace the filter material according to the site situation.
②Use differential pressure control.
The principle is: when the pressure difference between the front and rear of the filter reaches the upper limit of the set value, the differential pressure sensor outputs a signal to control the motor to rotate and start to replace the clean filter material. When the differential pressure value reaches the set lower limit, the differential pressure sensor outputs a signal to control the motor to stop working.
The control system is equipped with a material end alarm signal. The equipment is equipped with a limit plate. When the clean filter material is about to be used up, the limit plate touches the limit switch, and a signal is sent out to alarm at the end of the material, reminding the staff to replace the filter material.