A technical requirement for bidding of roller shutter filter in a sewage treatment plant
The automatic roller shutter filter needs to be provided with an automatic roller shutter filter according to the size of the opening of the air inlet corridor of the blower room. The automatic roller shutter filter should use the special non-woven fabric as the filter medium, and use the pressure difference signal before and after the filter to control the automatic replacement of the filter material, without judgement. The automatic rolling shutter filter needs to adopt a flat structure to increase the effective filtering area.
Filtration efficiency class: European air filter G3/G4 standard
Dust holding value: ≥200g/m2
Ambient temperature: -20~50 oC, relative humidity 50~90% The control cabinet should have the following functions (not limited to this): power indication, time setting, differential pressure switch, filter material alarm indication.
HICLOVER is growing brand for environmental protection field, and market share with most of Africa, Middle East, Southeast Asia countries and part of North America, Europe territory. We are trusted partner for governmental organizations, non-profit organizations, international contractors, logistics organizations, military, pet cremation business owners, etc. We have export experience more than 40 countries, including war zone like Iraq, Afghanistan, Somalia, South Sudan. Mobile: +86-13813931455(WhatsApp) Website: www.hiclover.com Email: firstname.lastname@example.org Email: email@example.com
All buttons and indicators are equipped with Chinese and English signs, green for stop, red for running, yellow for fault, white for power indication, etc.
The filter material needs to have good comprehensive performance of ventilation and dust removal, low resistance, high strength, good temperature resistance and chemical stability, and non-toxic, odorless, and non-volatile.
The automatic roller shutter filter frame should be made of corrosion-resistant aluminum alloy or stainless steel.
The winning bidder for the magnetic levitation single-stage centrifugal blower should send a representative with rich experience in installation and debugging to inspect the installation and supervise and guide.
After the blower, motor, control system and all accessories are installed, each blower shall be subject to field acceptance test under actual operating conditions. The test is carried out by a representative of the blower manufacturer in the presence of the tenderee and its engineer.
A sufficient (more than 2 hours) no-load operation test should be carried out before the blower load test, and a full-range operation test should be carried out according to the specification.Site acceptance testing shall demonstrate that the blower is in any condition
– No damage during installation and shipping
– Installed correctly
– no mechanical defects
– good alignment
– Connect correctly
– No overheated parts
– No abnormal vibration and noise
– no overloaded parts
– no air leaks
– The protection device is sensitive and reliable. The corresponding experts of the winning bidder shall instruct users and their engineers on how to start, stop, maintain and troubleshoot the blower when inspecting the installation and conducting on-site tests.